The purpose of this Technical Specification is to provide technical guidance on the requirements for generating plants which can be operated in parallel with a distribution network. For practical reasons, this Technical Specification refers to the distribution system operator in case
settings have to be defined and/or provided, even when these settings are to be defined and/or provided by another actor according to national and European legal framework.
NOTE 1 This includes European network codes and their national implementation, as well as further national regulations.
NOTE 2 Further national requirements especially for the connection to the distribution network and the operation of the generating plant can apply.
The requirements of this Technical Specification apply to all generating plants, electrical machinery and electronic equipment, irrespective of the kind of primary energy source and irrespective of the presence of loads in the producer’s network that meet all of the following conditions:
converting any primary energy source into AC electricity;
connected to a MV distribution network;
intended to operate in parallel with this distribution network under normal network operating conditions.
NOTE 3 Generating plants connected to a LV distribution network fall into the scope of EN 50438 (up to 16 A) and CLC/TS 50549-1 (above 16 A).
Unless stated differently by the DSO, a generating plant with a maximum apparent power up to 100 kVA can, as alternative to the requirements of this Technical Specification, comply with CLC/TS 50549-1. A different threshold may be defined by the DSO. This Technical Specification defines connection requirements.