This corrigendum to DIN EN 50288-7 (VDE 0819-7):2006-03 corrected on page 10 under 4.16 Outer sheathing the last two paragraphs by the following new sentences: For cables without metallic protection, the minimum thickness at a point shall not fall below the nominal value by more than 15 % + 0,1 mm. The minimum average thickness, rounded to 0,1 mm, shall not be less than nominal thickness.
For cables with metallic protection (4.14), the minimum thickness at any point shall not fall below the nominal value by more than 20 % + 0,2 mm.
On page 17 under C.4 Crush factors, table C.4 is the third line to correct as follows:
Ind screen triples 0,939